Call T. J. Snow
Industrial Water Chillers
Benefits & Advantages
What is a chiller?
How to correctly size a chiller
How much am I spending on water?
Open Expansion Tank
For MTA TAEevo product line only
Facilitates cooling loop filling by manually pouring coolant into external reservoir
Provides a visual indication of coolant level and top-off convenience
Must be installed at the highest point of the coolant loop to avoid overflow possibility
Install components as shown making sure that valves A & B are open and valve C is closed.
Add water or water-coolant mixture into the tank opening D.
Continue filling slowly until a level is maintained at about half of the expansion tank volume.
Operate the chiller pump to circulate coolant throughout the coolant loop.
Add coolant as required to maintain a steady level in the tank and top off as needed.